- DC Input: 200% oversizing, 16A current, 40~450V wider MPPT voltage range
- Multiple interfaces for presenting data
- Mass management and broad extension via Datahub
- Support external Rapid Shutdown Device (RSD)
On-grid, or grid-tied, means the inverter can generate power when connecting to the grid. When the grid is disconnected or cut-off, the on-grid inverters will stop until the grid is back due to anti-islanding requirements.
We have single phase from 600W to 8kW, and three phase from 3kW to 150kW. For more details, please refer to this page: https://www.solaxpower.com/x1-boost
Yes, a meter or a CT is needed for export control(In the on-grid inverter series,only single phase on-grid inverters are compatible with CT,three phase on-grid inverters are not compatible with CT) . Once a meter or a CT is connected, you should configure the inverter via LCD screen(App for non-screen version). Go to setting item 'Export control' to enable meter(or CT) and then confirm how much power to inject to the grid. If you want zero injection, you just need to set the value to 0.
This is an aritcle about how to setup and overview 10s refreshed in SolaX Cloud platform and application.
This article is about how to use and set the Meter/CT self check function.
It expains what is Export Control, why need export control, how it works and how to setup on Solax Inverter.
This article explains the 3 Phase, 1 Phase of electrical distribution system knowledge and applicable voltage & connection for SolaX inverter.